We successfully passed our roof inspection today!
Sadly, we did not pass the electric inspection. The inspector was impressed with all the new conduit and wiring, but did not like our ground to the water pipe. To ensure the ground is never ‘accidentally’ removed when plumbing updates are made, we will need to re-route the ground to the main inlet (and run it in hard conduit). We also, will have to update the meter box and install an 8′ ground rod to bring it up to code. So today, we installed the ground, and Friday will loose our power for awhile to update the box and install the ground rod.
Back to the grind!